Question about Coleman Heating & Cooling
The ducane unit is a three ton unit operating off of R22 also its a single phase. The contacts work the fan works and I have 24 volts on the t-stat. Every now and then the compressor cuts on maybe once a week when. I need a list of things to check for
Do you have a humidistat or a setting on you thermostat to regulate humidity? that would do it regardless of the temperature.
other then that, the only thing that can close that contactor to run the compressor is the t-stat or loose wire/short of the yellow control wire with the red 24V.
Posted on May 31, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 29, 2017 | Carrier Heating & Cooling
Aug 03, 2011 | Goodman CKL30AR30 Air Conditioner
May 23, 2011 | Heating & Cooling
Aug 26, 2010 | Weather King Heating & Cooling
Feb 11, 2010 | Taylor 632-27 Ice Cream Maker
Jan 12, 2010 | Mastercool 67471 Evaporative Cooler Air...
Nov 20, 2009 | Plumbing
Jul 18, 2009 | Ingersoll Rand Type 30 Electric Driven Two...
May 09, 2009 | Amana Comfort Zone 12M32PBEH Air...
Aug 09, 2008 | LG BG8000ER Air Conditioner
Dec 10, 2017 | Coleman Heating & Cooling
67 people viewed this question
Usually answered in minutes!