Question about Bryant 463AAC005BA Air Conditioner
Fan just trys to come on but humms
The humming may be the compressor running. The fan on top of your A/C outside tower is the condenser cooling fan. If the fan motor will start when you give the fan blades a push, then the start capacitor is bad & needs replacing. If the motor won't start when you give the blades a push, the start windings on the fan motor are burned out, and the motor needs to be replaced. Don't let your compressor run without the cooling fan, or you'll likely have to replace the compressor too.
Posted on Mar 07, 2016
Check for bound motor
Posted on May 31, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 11, 2014 | Bryant Heating & Cooling
Sep 09, 2013 | Bryant Heating & Cooling
Aug 26, 2011 | Bryant Heating & Cooling
Jul 07, 2011 | Bryant Heating & Cooling
Dec 14, 2010 | Bryant Heating & Cooling
Sep 28, 2010 | Bryant 462AJC021BA Air Conditioner
Sep 24, 2010 | Bryant Heating & Cooling
Jun 15, 2009 | Ruud UBHC Air Conditioner
Jun 03, 2009 | Heating & Cooling
Jun 12, 2011 | Bryant 463AAC005BA Air Conditioner
203 people viewed this question
Usually answered in minutes!