Question about Hayward H Series Induced Draft Abg 100,000 Heater
Our pool heater seems to be clicking and shaking after we turn on the heater. Checked filter and pressure - starts up fine, heats water, but clicks and shakes.....need help! Should we not run the heater while it is shaking?
Your pool chemistry is likely out of balance and leaving a residue on your heat exchanger coils. Had the same exact problem. Called a technician out and he said that I needed a new Heater after talking to Hayward. No warranty situation for sure. I went to the pool store, got 2 pieces of hose and hooked it up through my pump. Put a coil cleaner mixed with industrial vinigar and ran it for two days and all is good now. Solution after that was simply good chemistry in the pool. Salt water pool by the way.
Posted on Sep 20, 2012
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Actually, the clicking is likely causing the shaking. Inside the manifold of a H100 is a stainless steel diverter plate that send some of the passing water into the heat exchanger and lets the rest past and back to the pool. When it breaks, you will hear a 'clicking' noise at it rattles in the water path. When it breaks, the flow to the heat exchanger is intermittent and you will begin to boil the water, causing the shaking. This situation is dangerous, especially without a pressure relief in the heater or pipe. As long as your water chemistry is sound, Hayward will usually cover this under warranty even if the unit is over a year old. Contact them to get a factory authorized repair rep out at: http://www.haywardnet.com/locator/
Posted on Jun 12, 2009
Tips for a great answer:
Jun 09, 2013 | Hayward 100,000 BTU Pool Heater H100ID1 -...
Aug 05, 2012 | Hayward Pool & Spa
May 07, 2010 | Hayward H Series Millivolt 250,000 Btu...
Sep 21, 2009 | Hayward H Series
Aug 03, 2009 | Hayward H Series
May 27, 2009 | Hayward H Series Induced Draft Abg 100,000...
984 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: