Question about Weather King 10AJA2501AH Air Conditioner
My Central Air unit will not stop running. The blower inside will kick off when the temperature gets down to the specified limit, which happens fairly quickly. The air coming out is very cold and appears to be working properly, but the Compress will only stop when I flip the breaker.
Sounds like the contactor is stuck in the outside unit. Turn off the breaker or safety switch, remove the cover, and tap on the body of the contactor with a hammer handle or similar tool. If a click is heard you may have dislodged it and it may work for either a short time or indefinitely. (yeah ,I know that's kinda vague) Test it. If that doesn't clear it up, disconnect the thermostat wires just to make sure and re-test. If the compressor starts without the thermostat connected, you will need to replace the contactor. If you feel real handy, you could perhaps remove the cover, seperate the contacts with a screwdriver, dress the contacts with an emery board until smooth and shiny, and try again.
Posted on May 24, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 22, 2014 | Carrier 3 Ton Infinity Puron A/c outside...
May 20, 2012 | Heating & Cooling
Apr 05, 2011 | Heating & Cooling
Dec 09, 2010 | Ruud Central System Air Conditioner
Jul 17, 2010 | Heating & Cooling
Jan 15, 2010 | Omega Trane Furnace Draft Inducer Blower...
Jul 26, 2009 | Heating & Cooling
Jun 03, 2009 | Heating & Cooling
Jul 27, 2008 | Carrier 38CKC036 Air Conditioner
1,299 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: