Question about Weather King 10AJA3001AH Air Conditioner
You don't have the t'sat wires to the outdoor unit hooked up. They should be on the y & c terminals. If they are you may have a burnt out contactor coil. It should read 24volts at the contactor coil when you are calling for cooling
Posted on Jun 03, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 06, 2016 | Heating & Cooling
Dec 26, 2013 | Heating & Cooling
Dirt is the biggest enemy of your furnace. It can waste fuel and drastically lower efficiency. Dirt affects all three basic components of your furnace, so cleaning is the most important part of regular maintenance. The three parts of the furnace should be cleaned: the filter system, the blower, and the motor.
The furnace filter should be replaced or cleaned at the beginning of the heating season and about once a month during periods of continuous use. To check the filter, take it out and hold it up to the light. If it looks clogged, replace it with a new filter of the same type and size regardless of the length of time it has been used.
Step 4: Clean blower assembly, belts and pulleys to blower, and motor housing. Cleaning blower is critical if furnace has a squirrel-cage fan, because openings in this type of blower often become clogged with dirt. To clean blower, remove panel that covers filter to gain access to blower or panel on front of furnace. This panel may be slip-fit on hooks or held by series of retaining screws. Access to inside of blower is usually gained by sliding out fan unit, which is held on track by screws.
If power cord to fan assembly is not long enough to permit fan unit to slide all the way out, disconnect cord. Mark wire connections first so you'll be able to reassemble unit correctly. With toothbrush, clean each fan blade and spaces between blades. Then, with vacuum cleaner hose, remove all dirt and debris loosened by brushing. Vacuum belts and pulleys. Wipe motor housing clean to prevent heat buildup in motor.
Feb 08, 2013 | Rinnai Toyostove Direct Vent Heater:...
Mar 11, 2017 | Ruud UBHC Air Conditioner
Jun 13, 2011 | Intertherm Heating & Cooling
Jan 19, 2018 | Honeywell Heating & Cooling
Oct 22, 2010 | Heating & Cooling
Jun 30, 2010 | Refrigerators
Dec 06, 2009 | Heating & Cooling
112 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: