Question about Heating & Cooling
GAS NOT FLOWING THROUGH REGULATOR WHEN PILOT ENGAGED MANUAL LIGHT NO LIGHT NO GAS WHEN PUSHED
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Procom ML200TBA
Propane appliances usually run on 10-11 inches of water column, this is about 1/2 pound of pressure. If the regulator you have is not rated for delivering gas at that rate, you will need to find one that does. If your regulator is rated for more than the 11 inches, most likely you could have damaged the appliance regulator that came with the heater. Check the propane pressure specified by the heater manufacture against the rated supply of your regulator and see if they match. Make sure the heater is rated for Propane and NOT Natural Gas. Check to see if the gas valve on the appliance is in the operate position and all valves are open. Bleed off the air in the gas line by holding down the pilot switch and keep attempting to light the pilot. It could take you a few minutes. If you hear and smell gas but the unit will still not light, don't chance at getting hurt, call a technician. Look to make sure there are no safety switch that may have triggered off not allowing the gas valve to operate. And make sure there is no obstruction in the heater?s gas valve blocking off the supply of gas. Always exercise caution when it comes to gas and if you are uncomfortable, call a qualified gas technician.
Posted on Sep 17, 2007
SOURCE: Unable To Keep Pilot Light Lit!
I have a Williams top vent gravity wall furnace (model 5009622) and I had the same problem. I had to take the cover off the furnace -- screw on top and two at the bottom (open the access door and there is one screw on each side) to get to the reset button for the vent safety shutoff system. On my furnace it's on the left side toward the top of the unit. I pressed the little red reset button and it's been working ever since. If your furnace is properly installed and doesn't have bird's nest in the chimney, it should work fine. Good luck!
Posted on Dec 06, 2007
SOURCE: Gas wall heater won't light
You need to bled the line longer and when you get lited hold down for a good minute.When the gas gave out ,there could trash in the line.I would take the line off and blow gas through it undtil you can smell it.
Posted on Mar 13, 2009
Check the connection of the thermocouple or replace it if connections are tight.Pilot safety valve may be badreplace gas control valve.
Posted on Oct 24, 2009
Tips for a great answer:
Jan 05, 2015 | Heating & Cooling
Nov 03, 2014 | Heating & Cooling
May 09, 2011 | Hotpoint RGB528 Gas Kitchen Range
Dec 09, 2010 | Rheem Water Heaters
Nov 20, 2010 | Heating & Cooling
Sep 13, 2010 | Reliance Water Heater #6-40-GBRS 40GAL...
Apr 26, 2010 | Heating & Cooling
Jan 30, 2010 | Napoleon 36" Zero Clearance Top/Rear Vent...
Jan 04, 2010 | Whirlpool GS460 Gas Kitchen Range
Oct 05, 2009 | Rinnai Desa Vent-Free Infrared Gas Heater:...
87 people viewed this question
Usually answered in minutes!