Question about Comfortmaker Heating & Cooling
I have no heat coming through my vents yet I heard my igniter click and ignite but no air comes thru vents
Most furnace operating on Oil or gas will heat the combustion chamber before starting fan to prevent cold air draft at start-up, can last a minute or two. Eiter the main flame does not come on or the chamber thermostat have fail. Try to modify fan option on room thermostat from auto to on. Cold air coming out: burner problem or no more oil or gas, warm air: burning chamber thermostat problem, leave room thermostat fan option to on until repair.
Posted on Jan 03, 2014
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
the fan you hear come on at a call for heat is most likely just the inducer motor. the click you hear is probably the relay for the hot surface ignitor which should glow red, then in turn ignite the main burners. your going to have to determine if the ignitor is coming on. if it isnt the ignitor is bad and will need to be replaced. if it comes on and than shuts off after a few seconds the ifc board is probably at fault
Posted on Apr 10, 2009
Tips for a great answer:
Jan 01, 2016 | Heating & Cooling
Oct 13, 2013 | Heating & Cooling
Jun 05, 2013 | Coleman Home Electric Furnace Eb15b/Eb15d
Oct 08, 2012 | Heating & Cooling
Jan 29, 2010 | Heating & Cooling
Nov 07, 2009 | Ruud Central System Air Conditioner
Apr 09, 2009 | Heating & Cooling
260 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: