Question about Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
your make up water pressure is greater than the safety relief pressure. The safety should be 30psi lift. the makup usually goes through a regulator called an automatic makeup valve. these valves operate infrequently on a closed system and get rusty. They stick. If yours is stuck open, then your makeup water pressure which is probably greater than 30psi is overpressuring your boiler.
Posted on Sep 30, 2008
It sounds like an air lock. Try this: With the machine off, connect the hose to the washer and let it run for several minutes to get all of the air out of the hose, and to purge any air out of the pump. Shut off the water, and connect the high pressure hose, but not the gun. Let the water run for several minutes. stretch out the HP hose and make sure that the air is displaced. Shut off the water, connect the gun, and purge as before. Now crank it washer up. As quickly as safe to do so, open the trigger to keep water moving through the washer. It should come up on pressure very quickly. It is better during normal operation to keep water moving through the system. When I am through for a while, I shut down my washer, but leave the trigger depressed to allow the pump to stay full of water, and cool. This prevents further problems when I restart it.
Hope this was useful.
Posted on Jul 17, 2009
SOURCE: leaking pressure relief valve
what is the water pressure on the cold side? You may need to install a pressure reducing valve at the water heater inlet to reduce inlet pressure and keep pop off valve from opening when not needed.
Posted on Mar 10, 2010
The pressure switch has gone bad....there is a switch that is to stop it and then restart it on pressure...either the switch is bad or the tube is plugged...going to the switch.
Posted on Sep 14, 2010
Tips for a great answer:
Sep 13, 2015 | Water Water Heaters
Mar 19, 2015 | Water Water Heaters
Feb 15, 2011 | Rheem Water Heater Pressure Relief Valve
Hot water pressure relief valves serve two functions. The first is to remove high-pressure water from the hot water tank. The second function is to act as a high temperature valve to remove water that exceeds a predetermined point for the valve. Both of these relief settings are preset at the valve factory. Many pressure relief valves will come with a metal tag that identifies these release points. If you're attempting to remove the hot water heater pressure relief valve, pay careful attention to ensure that you replace with the correct valve.
Your hot water heater has a pressure relief valve safety mechanism. When pressure inside the water tank exceeds certain limitations, the valve opens up to allow the pressure to be released. A faulty pressure relief valve will not release excess pressure, which could cause extensive damage to your home. You should test the hot water heater pressure relief valve once every six months to ensure proper operation. If the pressure relief valve fails the test, replace the valve with a new one immediately
Locate the pressure relief valve on your hot water heater. The pressure relief valve has a lever handle on top with a drain pipe attached to it. The pressure relief valve is most often on the side of the water tank toward the top. Newer models of hot water heaters have the pressure relief valve on top of the water tank.
Inspect the area around the pressure relief valve for signs of leaking water. If there is leaking water near the relief valve connection, replace the relief valve. If no leaking is evident, proceed with testing the pressure valve.
Examine the area below the pressure relief valve drain pipe. Most water heater closets either have a drain in the floor below the pipe or the pipe is inserted into another pipe to direct the water out of the home. If the end of your drain pipe is not in another pipe or there is no drain in the floor, place a bucket under the drain pipe to catch water when you test the pressure relief valve.
Pull the lever handle on the top of the pressure relief valve up with your fingers. A working lever will lift up without difficulty.You should begin to hear water going through the drain pipe. Slowly release the lever to shut off the pressure relief valve. The pressure relief valve is good. If you did not hear water running through the drain pipe, lower the lever on the pressure relief valve and replace the valve. If the lever is difficult to raise, do not force the lever. Replace the pressure relief valve.
Feb 04, 2011 | Whirlpool Water Heaters
Dec 19, 2010 | Rheem Water Heater Pressure Relief Valve
Nov 17, 2010 | Watts 3/4 Pressure Relief Valve
Mar 25, 2010 | Heating & Cooling
Jul 12, 2009 | RTO Atwood Water Heater - 6 Gal LP
Jan 13, 2018 | Heating & Cooling
Jun 18, 2018 | Heating & Cooling
36 people viewed this question
Usually answered in minutes!