Question about Dayton Heating & Cooling
Pilot will light, but when plunger is released stops releasing gas
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Unable To Keep Pilot Light Lit!
I have a Williams top vent gravity wall furnace (model 5009622) and I had the same problem. I had to take the cover off the furnace -- screw on top and two at the bottom (open the access door and there is one screw on each side) to get to the reset button for the vent safety shutoff system. On my furnace it's on the left side toward the top of the unit. I pressed the little red reset button and it's been working ever since. If your furnace is properly installed and doesn't have bird's nest in the chimney, it should work fine. Good luck!
Posted on Dec 06, 2007
SOURCE: Pilot light won't stay lit
Look for dust and lint. Look for them in places where gas should be freely flowing. I had a similar problem with an Empire Corcho wall-mounted propane ceramic catalyst heater. First it was the pilot light, then the #2 ceramic mantle. After horsing around with the gas lines and pressure regulators and trying to re-aim the pilot, it all turned out to be dust and lint in the gas passages. A little dust bunny in the brass pilot tube gave me a pilot light the shape and color of a banana. One puff of compressed air, and I got back my razor-sharp pilot. And some dust in the chimney of the #2 burner kept it burning blue/yellow and blistering paint off the upper surfaces of the heater. A bit of cleaning with a shop-vac put that right. "Passive" heaters are very much prone to this sort of problem because they rely on convection currents (i.e. LOW velocity) to get the job done. Convection currents are notorious dust collectors, as in COBWEB CITY.
Posted on Feb 28, 2009
The power pile (pilot generator) is defective. It produces a milivolt signal to ensure to keep the gas valve open. If it goes bad, the valve thinks the pilot is out, even when you are holding the button down, so when you release the button, it shuts the gas off to prevent excess gas buildup and a possible explosion.
Posted on Sep 12, 2009
Tips for a great answer:
Oct 28, 2013 | Vanguard Heating & Cooling
Jul 27, 2017 | Heating & Cooling
Sep 04, 2010 | Leisure HOMEPRIDE Electric Fireplace...
Jan 11, 2010 | Reddy Heater RLP100 Portable Forced Air...
Nov 30, 2009 | Heating & Cooling
Nov 17, 2009 | Heating & Cooling
Sep 12, 2009 | Reddy Heater RLP100 Portable Forced Air...
Aug 08, 2009 | Teledyne Laars Laars Lite 2 Pool Heater...
40 people viewed this question
Usually answered in minutes!