Question about Fedders A6D24E7D Wall/Window Air Conditioner
Suddenly no cooling but fan running, also remote does not work nor does the control panel on the unit, display shows 10 which i think is a delay option
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Fedders Window AC
You may have thermostat problems. If the blower and compresssor kicks on, that indicates their ok. If you have a two wire thermostat, you can tie those wires together to see if the unit will operate. BE SURE TO DISCONNECT POWER.
Posted on Aug 18, 2007
you need to check the fuses at the disconnect near the condenser outside. if they are blown then replace. Be very careful this is typically 208 vac and will hurt ya. If the power failure occured and then came back on soon, the unit needed to equalize and tried to start under a load. The remedy for this is to install a time delay on cool call about 2 minutes. they sell thermostats for this or you can install an adjustable delay inline with the yellow wire going to the contactor on the condenser.
Posted on Nov 24, 2009
Tips for a great answer:
Jul 21, 2015 | Dometic Rooftop RV Air Conditioner
Aug 29, 2011 | 1991 Mercedes-Benz E-Class
Jul 22, 2011 | Amana Heating & Cooling
Mar 07, 2011 | 1995 Kia Sephia
Jan 19, 2011 | Heating & Cooling
Jul 07, 2010 | Whirlpool ACQ122XK Air Conditioner
Apr 06, 2010 | 1996 Chevrolet Monte Carlo
Jun 11, 2009 | Goodman CKL60AR60 Air Conditioner
Jun 09, 2009 | Haier ESA306 Air Conditioner
29 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: