Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
That is not the case for Goodman defrost boards. You have to first jump the R and DFT on the board to give 24v to the DFT, then take your factory jumper, on 30 from factory, and jump the test pins, as soon as you hear the board click, remove the jumper from the test pins. It is suppose to stay there a max of 10 mins or until you remove the 24v from the DFT terminal. 3 things should occur, 1-fan relay opens stopping fan, 24v is applied to W2 and O. I work at Goodman.
Posted on Jan 17, 2010
Tips for a great answer:
Jan 29, 2016 | Goodman Heating & Cooling
Jan 08, 2015 | Goodman Manufacturing Goodman GPH1543M41...
Jan 08, 2013 | Goodman CLQ36AR49 Air Conditioner
Dec 27, 2009 | Goodman GMS90703BXA Heater
Dec 22, 2009 | Heating & Cooling
Jul 11, 2009 | Heating & Cooling
Apr 27, 2009 | Goodman CLQ36AR49 Air Conditioner
Nov 11, 2008 | Goodman Heating & Cooling
29 people viewed this question
Usually answered in minutes!