Question about American Standard Cadet 3 Right Height Elongated Toilet by - ADA Compliant
Bits of tissue are still in the pan after its been flushed
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The tank holding the proper amount of water is a good sign. The inside of the stool is like the GOOSE NECK under you sink. It always holds water. This may sound like a bit of a hassle to do but if all 3 toilets are identical, here is what you can try if you are a bit handy. Go to the hardware store and purchase 4 toilet wax rings with a plastic flange and a few sets of toilet floor flange bolts(they are cheap and you can always return if not used, as It is better to have xtra parts on hand). Turn off the water supply to the "Mystery Toilet". Leave the tank and everything connected to the stool. Flush the toilet and remove all excess water from the tank and bowl. This can be done with a shop vac, sponge or towel. Disconnect the water supply to the tank. Remove the bolts holding the stool to the floor and carefully remove toilet. Scrap off all the old wax from the floor flange and bottom of stool. Now go and repeat this proceedure to one of the toilets that is working properly. In other words Switch the "Mystery Toilet" with a "Working Toilet" and see how they react. If the working toilet does it in the same bathroom and the "Mystery Toilet" does not do it in the other bathroom then you probably have a VENTING PROBLEM. If the "Mysery Toilet" Does it in the other bathroom then you most likely have a Defective Toilet. This Job is best done by 2 people, as it can sometimes be challenging to center the new wax ring on the toilet flange. Reconnect to the floor and reconnect water supply to the tanks. DO NOT OVERTIGHTEN BOLTS to the floor flange as you may crack the toilet. All drain lines must be vented properly for water to flow. If you are curious check out drain venting on the internet. Also, sometimes a vent can become obstructed with debris, ice, bird nest, etc.. I would 1st check the vent on the roof visually and then have someone flush and listen. If you believe the vent is clear....Then do the toilet switch and go from there.....Hope this helps and Happy Holidays....Joe
Posted on Dec 21, 2008
After working for ROTO-ROOTER for 20 + years, I have come across this problem more than twice. There are many problems that can be included, but let's start with the most simple and go from there. Step 1... Check your roof vent to see if it is obstructed with debris, such as birds nest, frozen ice, dead animal...etc..... To check this you must go onto the roof and find the sewer vent(it is not hard to find as it smells like sewer). Visually look into the vent even using a flashlight to make sure there is nothing obstructing the vent pipe. certain things can clog your vent such as Debris,Birbs Nest, Ice, dead animal,Etc..A drain line needs a air vent so water can flow....If nothing is visually seen , have someone flush the stool. If you cannot see any obstructions and HEAR THE FLUSH, Your Vent is okay. Check out plumbing and venting on the internet for more reference. If this is not your problem then you must pull the stool and see if there is an object stuck in the toilet......Comb, toothbrush, Etc... The best way is to pull the stool from the floor and look from the bottom of the toilet to see if there is an object stuck inside the stool.Turn off the water supply and disconnect it from the tank. Go to your local hardware store and buy 2 wax rings with plastic flanges and a set of flange bolts(these are cheap and can be returned if not used).Turn off the water supply to the toilet tank and flush it to drain all the water from the tank and the stool. You can use a shop vac or an old towel to remove the water. After removing the stool, lay it on its side and look from the bottom to see if there are any obstructions. You may need a mirror and flashlight to see inside the gooseneck of the stool. If you cannot see any obstructions, you can try to dump a 5 gallon bucket of water through the bottom of the stool to push the object out the way it entered. NOTE: When reinstalli8ng the stool, be careful not to over-tighten the floor flange bolts as you might crack the toilet......Joe
Posted on Jan 02, 2009
You are probably correct, the water level needs to be raised. There are many different toilet tank systems, but all have some way to control the water level in the tank. Let me know if you need help figuring it out...
P.S. You'll have to take the lid off the tank, first...pardon me if that is too obvious
Posted on May 08, 2009
Tips for a great answer:
Jan 22, 2015 | Saniflo Home
Sep 04, 2011 | Caroma toilet - water saving Sydney Low...
Dec 11, 2010 | Saniflo SaniPlus-Round SaniPlus Macerator...
Dec 10, 2010 | Home
Jul 05, 2010 | Saniflo SaniPlus-Round SaniPlus Macerator...
Aug 24, 2009 | Saniflo Home
Aug 09, 2009 | Saniflo & Saniplus& Macerator Pump
Jan 27, 2009 | Saniflo & Saniplus& Macerator Pump
Dec 19, 2017 | American Standard Cadet 3 Right Height...
119 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: