Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
After four years I do not thing you have an effective warranty even if the company still in business. you need to open it first and clean it from any builod up dust and check the switch to see if it is working (thermostate)
Posted on Nov 08, 2009
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose, Dirty Air Filter), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Posted on Mar 04, 2010
Tips for a great answer:
Mar 02, 2017 | Gibson Heating & Cooling
Jan 22, 2017 | Gibson Heating & Cooling
Feb 23, 2014 | Gibson KG7SA045C23A 45,000 BTU 80% Gas...
Oct 19, 2013 | Gibson Gas Furnace 60000 Btu 90% Afue...
Look on the back of the bottom cover... it should tell you what the blinking means...
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Feb 03, 2011 | Gibson Heating & Cooling
Nov 29, 2010 | Heating & Cooling
Apr 27, 2010 | Heating & Cooling
Apr 06, 2010 | Heating & Cooling
Mar 31, 2010 | Coleman Heating & Cooling
Nov 08, 2009 | Heating & Cooling
49 people viewed this question
Usually answered in minutes!