Question about Heating & Cooling
Hi try this link and go to page 16 fault finding it should give you a clue, I think it may just need bleeding. http://www.bhspares.co.uk/wp-content/themes/RevampV3/manuals/Worcester%20Bosch/DanesmoorSLPJ15-19.pdf Cheers Andy
Posted on Dec 30, 2013
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: My oil boiler is a
The actual final solution was to replace the fuel valve/solenoid following which the boiler has run without failure.
The conclusion was that the fuel valve solenoid was ok when cold but when heated up had some sort of electrical breakdown in its coils, causing the fuel valve to fluctuate until the boiler locked out.
Posted on Oct 17, 2008
Tips for a great answer:
Dec 21, 2015 | Ovens
Oct 06, 2017 | Water Heaters
Jan 27, 2018 | Heating & Cooling
Sep 05, 2010 | Heating & Cooling
Oct 20, 2009 | Water Heaters
Jul 23, 2009 | Water Heaters
Jan 19, 2009 | Water Heaters
Oct 04, 2008 | Heating & Cooling
Nov 24, 2017 | Honeywell Programmable Thermostat Heater
93 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: