Question about Honeywell he225h8908 bypass humidifier,12 gpd,w/ humidistat
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I am having the same problem. I have had my humidifier for about 5 years now and I just started having the problem where the water continuously flows through the solenoid. I took apart the solenoid by removing the fittings from both sides. When I did that, I noticed that there was a hole in the metal that allowed me to see through to the other side. Apparently, it had corroded and and broken through, allowing the water to pass through the solenoid without really going through the valve within the solenoid. There are several sites that sell replacements for about $70, which is not cheap, but cheaper than buing a new humidifier for $120. Here is one site I found: http://www.iaqsource.com/product.php/honeywell/32001639-002/?product=112783&category=1142
Posted on Nov 20, 2008
Check for 24volts at the valve. Some techs install these so it only comes on when the furnace calls for heat. It should have its own transformer.
Posted on Jan 19, 2009
SOURCE: No Water flow thru Humidifier
Loosen the brass fitting where it connects to the soleniod valve. If water comes out your saddle valve is ok. Carefully retighten this fitting. With the humidifier turned on loosen the first fitting down stream from the valve see if water comes out. if it does turn the humidifier off and see if it stops, it should. That will tell you the the valve is ok then, just clean the filter and the oriface. if it does not turn on and off check the wiring. if ok replace the valve.
Posted on Mar 29, 2009
Tips for a great answer:
Feb 09, 2011 | Honeywell HE220A1019 Whole House...
May 27, 2017 | Honeywell HE225B Humidifier
Dec 20, 2010 | Honeywell HE220A1019 Whole House...
Apr 17, 2009 | Honeywell HE365 Humidifier
Jan 02, 2009 | Honeywell HE220A1019 Whole House...
Nov 22, 2008 | Honeywell HE365 Humidifier
Dec 28, 2007 | Honeywell HE220A1019 Whole House...
Nov 30, 2007 | Honeywell HE360A1027 Whole House...
211 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: