Question about Carrier Heating & Cooling
My 70y old dad wants me to take 2 carrier 3 ton package units and make a good one. the wire diagram is gone on both units i was electrican, comerical new buildings, he started with out me and unpulged and moved motors, coil ,transformers i just need a wire diagram were all wire's plug in to
I assume you know if this is correct voltage and single or 3 phase, and whether it will fit your application or not, how is the duct work going to attach, how many people will be in the conditioned area, what is the building made of, how much insulation is has...
A little more to it than just "turn it on".
If you get the models and serial and can contact the manufacturer or their representative you might get a wire diagram. Most any package unit would do. As long as you keep the original equipment controls. If you "patch" it up it may be hazardous by not having safety's where it was designed for. Or for instance It may have a anti freeze thermostat. By passing this could lead to coil freeze up and compressor damage. Leaving out a pressure switch (if any) may do the same or could become dangerous to people in the event of fan motor failure. A low temperature fan speed switch may not be needed now unless you plan to run the AC in below 55'f.
And a few dozen other factors that might need to be considered.
If you feel confident after this then contact carrier.
Please rate me as high as you can and thanks for using fixya.
Posted on May 19, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 20, 2016 | Gibson Nordyne/2 Ton Heat Pump Package...
Dec 29, 2015 | Cars & Trucks
Aug 29, 2017 | Carrier Heating & Cooling
Jan 26, 2014 | Heating & Cooling
Aug 17, 2012 | Goodman Heating & Cooling
Apr 09, 2011 | Heating & Cooling
Apr 03, 2010 | Heating & Cooling
Jan 11, 2010 | Heating & Cooling
Nov 21, 2009 | Heating & Cooling
Jun 05, 2009 | Heating & Cooling
538 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: