Question about Heating & Cooling
You'll need a clamp on style ammeter to check it. On the data plate of the unit, look for the "LRA" Locked Rotor Amps value. Clamp the jaws of the ammeter around just one of the large black wires connected to the compressor and try starting the unit while observing the reading on the meter. If it's close to the value on the data plate, then your compressor is indeed locked. A bad start capacitor could be the culprit too
Posted on Jan 05, 2014
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 11, 2017 | Cars & Trucks
Nov 22, 2014 | Mitsubishi Cars & Trucks
Jan 07, 2013 | 2003 Toyota ECHO
Aug 03, 2011 | Whirlpool CA24WCR Thru-Wall/Window Air...
Jan 31, 2011 | Mitsubishi Heating & Cooling
Jan 11, 2011 | LG LSC183VMA Split System Air Conditioner
Dec 16, 2010 | Haier HWR12XC5 Air Conditioner
Feb 20, 2010 | Comfort-Aire MSH-024 Air Conditioner
Jan 29, 2008 | Heating & Cooling
Oct 26, 2007 | Heating & Cooling
120 people viewed this question
Usually answered in minutes!