Question about Raypak Free Hydraulic Lift Gate Delivery - No L...
Where is the pilot light on Raypak versa pool heater
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: pool heater wont fire up
Its just after 1 am here as well, Ontario Canada. Yes, you have to remove the front lower panel by raising it then pulling out at the bottom. Then compare the valve you have with the 2 in the picture on pg 5. If it is easier, you can have your husband call me while doing this and I can talk him through it. My contact information is located on the main page of my company website www.emshvac.com
Posted on Jun 23, 2009
Often you can see the pilot if you use a small mirror. With the button on the gas valve pushed down you should get pilot. Once the pilot is lit it warms the TC(thermocouple) creating the static charge to open the gas valve on it's own. The TC is set in the pilot assembly. It will be a small tube like piece with the wires coming from it. Some times you can pull and replace it but I will usually get the whole pilot assembly and just replace that. It will probally be rusted and can be cloging the tiny orface on the pilot itself.
If you have a milivolt meter you can check the TC by pulling the wires that come from it at the gas valve and with the button on the gas valve pushed in and a good flame you should get 500-700 MV from the TC. This is 1/2 a volt+ so you will need a MV meter. But this will tell if your TC is bad or if your valve is bad.
Posted on May 13, 2010
Tips for a great answer:
Oct 11, 2014 | Raypak 2100 Pool Heater Gas 266000 BTU'...
Jun 15, 2014 | Raypak Pool & Spa
Jul 13, 2013 | Raypak Versa 130,000 Btu Above Ground...
Jul 19, 2011 | Raypak Versa 55k Btu Natural Gas Millivolt...
Jun 19, 2010 | Raypak Versa 130,000 Btu Above Ground...
Jun 10, 2010 | Raypak BURNER TRAY ASSEMBLY
Jul 11, 2009 | Raypak Versa 130,000 Btu Above Ground...
Jun 07, 2009 | Raypak BURNER TRAY ASSEMBLY
2,747 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: