Question about Panasonic VS6 Cellular Phone
I lost my cover and I need a supplier. No one at Panasonic US seem to be aware that a model called EB-VS6 exists. They maintain that it is either Asian or EEC.
Can you help me
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: where can i find a back cover??
Link below for replacement cover
Posted on Dec 27, 2007
Tips for a great answer:
Jul 04, 2012 | Cars & Trucks
Jun 18, 2008 | Samsung Cell Phones
The fan replacement is not hard, but it is fiddly.
You need to pull out the battery case to remove DC power. To do this - front display cover off by pushing up the plastic tabs inside the bottom front of the cover and tapping the top of the cover to release the top tabs. Undo the screws on the metal plate which hold the battery in place. Take off the UPS outer metal case cover using a Torx screwdriver. Undo the 4 screws on the back holding the steel fan cover. Using needlenose pliers or a very small screwdriver, carefully remove the fan connector from the back PCB board. This connector is fragile and tends to break easily. Pull out the fan. Note the location of the 2 screws on the inside fan cover. I use a NMB-MAT Model 3610KL-04W-B50 12 volt DC replacement fan that I order in specially from any wholesale electronics shop as you want the maximum CFM out of the fan. You need to cut the existing fan leads and solder the existing connector leads to the new fan lead, using heat shrink tubing. The connector goes back in only one way- note the dimple on the side. The leads can be a little longer on your completed fan assembly. The fan manufacturer's label should face the back of the UPS.
This solution is for a PW9120-1500. I assume your UPS is PW9120-3000 or larger. Check the model of the existing fans.
Feb 24, 2011 | Powerware 9120 UPS System
Dec 20, 2017 | Panasonic EB-x400 Cellular Phone
Nov 15, 2007 | Nikon Laser 800 Rangefinder
Jun 23, 2006 | JVC Cybercam GR-D72 Mini DV Digital...
Nov 27, 2009 | Panasonic VS6 Cellular Phone
233 people viewed this question
Usually answered in minutes!