Question about Heating & Cooling
My first thought is, if you have to ask this question, you should not be playing with your HVAC because you will likely hurt yourself. But if you insist; What does the humidifier require 120 or 24V? If it is 24V, then you take it after the thermostat at the relay that turns on the rest of the system. If the humidifier wants 120V, take it from the switched portion of the above mentioned relay. Your heat pump is 240V, so one side of the humidifier goes to the relay, the other side goes to ground, not the other side of the 240V return. If your heat pump is connected through a GFI, this will likely trip the GFI, shutting down your heat pump.
Go download http://www.trane.com/webcache/un/split%20system%20air%20handlers%20%28ssa%29/product/12-1054-05_04012001.pdf
Go to page 12. 24V should be terminal 6 and A on the relay. 120V should be between B and ground on the fan motor. Before opening anything, turn all the breakers to the heat pump, likely 3 dual gang breakers. Have a couple spare automotive ATO 5A fuzes in case you blow one. Have an shut-off valve for the water supply. Please be careful!!! What you are doing has a high potential of hurting yourself or blowing up something in your heat pump, leaving you without heat.
Posted on Dec 28, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I would check the house thermostat(and its wiring to the indoor unit), and if it's OK then check the heat transfer fluid diverter valve inside the indoor unit (should be sending the hot fluid through the big radiator (air exchanger)) until the surface temperature of the radiator is approximately 130 degrees F, then the fan control operates and the fan starts to blow hot air through your ductwork. My HTM is 26 years old and I've had many opportunities to "hone" its operation...
Posted on Sep 24, 2008
SOURCE: amana furnace
This is no doubt due to failure of the "hot surface ignitor". This device lights the main burners for your furnace, and they fail a lot. I strongly recommend the replacement should be done by a technician.
Posted on Oct 25, 2008
It is normal. Your house has to go down a couple more degrees because the heat pump is not working. You can solve this by rewirng you thermostat. Take off the wire that goes to Y and tape off. Then take the wires that are marked w and e or w1 and put the wires to yellow. Do not run ac with it wired like this. If you need more information please post me back
Posted on Nov 29, 2008
Look at your Thermostat wiring.
If there is a green wire going to the "G" terminal, disconnect it.
If it stops running, you have a bad T-stat.
If it keeps running, you either have a stuck fan relay or a low voltage control wiring malfunction.
Those are usually related to one of the safety switches having problems.
If green is not going to G, let me know, and we will determine which one is indeed the fan wire and go from there.
Remember, when you rate the solution, it closes further dialog, so only rate when you are satisfied with the discusion.
Thanks for visiting FIXYA!
Posted on Jan 03, 2009
Tips for a great answer:
Nov 28, 2013 | Amana Heating & Cooling
Apr 19, 2011 | Amana Heating & Cooling
Jan 28, 2011 | Heating & Cooling
May 10, 2010 | Intertherm P3RA-036K Air Conditioner
May 07, 2009 | Heating & Cooling
Jan 11, 2009 | Honeywell Power Humidifier: Furnace...
Jul 02, 2008 | Amana PTH123B25AJ Heat Pump Air...
86 people viewed this question
Usually answered in minutes!