Water runs when furnace is off, but stops when furnace is on.
the 760 humidifier does not need a transformer wired externally. the 760 has its' own 24v transformer inside the fan compartment. this transformer will provide the power to enrgize the water solenoid as needed. it sounds like to me the additional trasnformer is hot all the time. when the furnace comes on, the unit gets power and the internal transformer is cancelling the power from the external transformer. this would explain why it quits running when the heat is on. since the external transformer is hot all time, when the heat shuts off, the solenoid is getting energized by the external transformer. to make this run correctly, you need to get rid of the external transformer. leave the humidifier high voltage wires hooked up so they are only hot when the furnace runs. if you have a humidistat that has a r and c terminal, you will need to wire these directly to the r and c on the furnace control board and move the switch inside the humidistat to "power". make sure it is not on "bypass". then wire your 2 brown wires from the humidifier to each of the "h" terminals on the humidistat. if you have a humidistat that only has 2 terminals, wire one brown wire to each of the terminals. this should allow it to run properly.
Jan 28, 2009 |
Aprilaire 700 Humidifier