Question about Bryant Evolution THERMOSTAT CONTROL SYSTXBBUID01-B VERSION 16
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Turn the power off to the Air handler unit.
Remove the thermostat from the wall, (Just the face part).
Look on the back side of the thermostat and verify that the jumpers are set to electric and not gas, otherwise the fan will not run during heat mode, they come from the factory usually set for gas.
If this is a electric heater this will solve your problem, If it is gas then it will be more detailed. Once you put it back on keep in mind that most thermostats have a 3-5 minute delay so just give it a little time and the fan should then work once you have the jumpers in the correct position.
Thank you for using FixYa!
Posted on Nov 17, 2009
Sounds like it is tripping on it's high pressure switch. This could be caused by a dirty condenser coil, overcharge of refrigerant, or non condensables in the system ( air most likely). I would get a second opinion from a repuatable company, sounds like he's trying to rip you off.
Posted on Sep 26, 2012
Tips for a great answer:
Jan 05, 2018 | Honeywell Heating & Cooling
Aug 21, 2015 | Bryant Heating & Cooling
Jun 02, 2014 | Bryant Evolution THERMOSTAT CONTROL...
Oct 31, 2013 | White Rodgers White-Rodgers 1F85RF-275...
Sep 25, 2012 | Bryant Heating & Cooling
May 09, 2010 | Honeywell Programmable Thermostat Heater
May 16, 2009 | Heating & Cooling
131 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: