Question about House Brand Heating&Air Conditioning Booster Fan
Hi, I have a new Brivis ducted heater but the installer never programmed the zones. It is a me30i. Does anyone know the step by step instructions to add the zones as buttons 4 & 5 dont even show the two zones. many thanks, Paul
Hi ill be honest this is a little tricky
There are many variations depending on a few things.
Is it heating only or add on refrig as well?
Is there a common zone or an area constantly open?
How many networker controls 1 or 2
So any way this is the set up for heating only 2 zones and common zone.
Turn the networker wall control off
in the off screen press the clock key (the time will flash)
hold down the 2 & 4 keys for about 5 seconds
depending on the model and what other appliances are lincked to it it will display either
H01 ID01 1500 (NC3 2004 onward)
1500 01 H01 (NC1&2 pre 2004)
press the (M or mode) button till you get to the N1 parameters eg N1 ID01 01
press the number 1 key or on older models top key
should then display should read
N01 ID15 01(COMMON ZONE)
Then using the dial to change the setting to read the same as below once done press the number 1 key or top key to advance to the next setting
press the number 1 key
N01 ID16 01(NETWORKER NUMBER)
N01 ID17 01(ZONE A)
N01 ID18 01(RELAY NUMBER ZONE 1)
N01 ID19 01(NETWORKER NUMBER)
N01 ID20 02(RELAY NUMBER ZONE 2)
N01 ID21 01(NEWORKER NUMBER)
then press the number 1 key followed by the on off button then, provided its all been installed correctly zones should appear and operate :-) good luck and i hope this helps.
Posted on May 16, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 07, 2014 | Cell Phones
Jul 26, 2013 | Cars & Trucks
Apr 25, 2013 | Heating & Cooling
Jul 12, 2010 | Heating & Cooling
Apr 12, 2010 | Heating & Cooling
Jul 25, 2009 | Honeywell Programmable Thermostat Heater
May 12, 2009 | Heating & Cooling
Feb 16, 2009 | Carrier 38BRC060 Air Conditioner
Apr 28, 2014 | House Brand Heating&Air Conditioning...
1,986 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: