Question about Hayward 250kbtu Ng Pool Heater - Inground
I would probably look at your high limit switches first and then at the bypass assembly inside of the header. The bypass controls the heat rise inside the heater. If it is bad, it may heat up too quickly, opening up one of your high limits. That will shut down the heater, once it cools back down, it will start again, and so on and so on.
Posted on May 22, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 20, 2017 | Washing Machines
Jun 27, 2014 | Hayward SAND FILTER, PRO SERIES
Jun 25, 2014 | Jandy Lite 2 Natural Gas Pilot Light...
May 28, 2013 | Pentair Meteor Above-ground 22" Sand...
Aug 12, 2012 | Hayward H-series Electronic Gas Pool...
Apr 12, 2011 | Hayward SAND FILTER, PRO SERIES
Apr 16, 2010 | Hayward SAND FILTER, PRO SERIES
Sep 02, 2009 | Hayward Pool Products HAYWARD H-Series In...
Jul 30, 2009 | Hayward Pro Series 18" Above Ground Pool...
161 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: