- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
4HP13/14 SPLIT SYSTEM HEAT PUMP .... indoor unit, outdoor unit contains system refrigerant charge for operation ... may be installed with up to 50 feet of line set (no more than ..... The defrost control incorporates 2 pressure switch .... Note: Sensor resistance decreases as sensed temperature increases. Pins/Wire. Color.Missing: tempstar
This Manual Supports Split Heat Pump Units of The Above Series .... two groups is based on a difference in Defrost controls and/or the .... completes a circuit between µRµ ? µOµ in the the thermostat sub-base. 2. .... before connecting line voltage. ...Wire "S1" is the first stage of electric heat through the outdoor thermostat.
Providing its a 24V controll circuit, any heat pump thermostat would do the trick. The real trick is finding one that goes down to 8 degrees. Make sure the range goes down that low, and that it's a heat pump thermostat. A lot of Honeywell thermostats work on both conventional, and heat pump systems. You'll have to read thru the installation instructions to program it from the default conventional setting, to a heat pump setting. The manuals are quite user friendly with pictures and everything! Good luck!