Question about Generac 40 Kw Natural Gas/propane Generator
New battery; 8 degrees outside; generator ran yesterday for several hours; propane tank 50% full
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If it was installed only five months ago, it should still be under warranty. Call Home Depot and have them send out a repair person.
Posted on Jul 01, 2009
throttle motor or governer board. or control board. your gas line could be to small. check the pressure while its cranking to see if it drops. watch the throttle to see if its moving while trying to crank the generator
Posted on Aug 28, 2009
Sounds like the electritian wired something wrong. Control wiring for that generator should be:
N1 and N2 = 240 vac utility input
Wire 0 = ground
Wire 194 (15B) = + battery
wire 23 = transfer signal
Posted on Oct 30, 2009
Tips for a great answer:
Feb 08, 2016 | Generac Guardian Air-Cooled Standby...
Dec 12, 2015 | Generac GUARDIAN Standby Generator 10 kW/9...
Nov 08, 2013 | Generac Electrical Supplies
Oct 17, 2013 | Generac 40 Kw Natural Gas/propane...
Oct 12, 2013 | Generac Guardian Electrical Supplies
Oct 28, 2012 | Generac Gp7000e Portable Generator
Sep 21, 2017 | Electrical Supplies
Sep 08, 2009 | Generac 100 Amp 120/240-Volt Transfer...
Jun 27, 2009 | Generac Guardian 200 Amp Transfer Switch...
38 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: