Question about Heating & Cooling
Change the flame sensor, check the connections on the sensor are tight , check pressure switch , check air filter is clean .
Posted on Jul 05, 2017
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Ok, you either have a inducer fan issue or a pressure switch issue or a plugged vent pipe. The inducer turns on to establish a draft for the exhaust. If it is not working you will get this error code. If the pressure switch does not sense pressure caused by the inducer, it will give this code. If either the intake pipe or exhaust pipe is blocked (even y just a little) it will give you the same error code. If the condensate hose or receptical is plugged, again it will give you this error code. Good Luck!
Posted on Oct 21, 2008
check to see if your intake pipe or vent is clear this could cause a flame jump and make it look like a bad flame sensor let me know if this helps
Posted on Jan 08, 2009
i need help rplce thrmostat with a digital braueburn my furnance wont turn on no flashing lights cant reset the burner though has power what do i do shoul i reset the circut breaker that was never tripped though
Posted on Jan 26, 2009
Thanks for your question,
The flame sensor eye is located just under the transformer, it is looking straight down the burner assembly to where the burner chamber is at, you will have to remove the entire assembly to get to it, first make sure the power is off, remove the transformer, then remove the entire burner assembly from the furnace cabinet, once removed you can see the flame sensor window, use a clean oil free cloth to clean it, it would probably be a good idea while you have it out to replace the burner nozzle, as over time they will clog, I hope this helps you fix your oil burner, let us know and rate this please, thanks again,
Posted on Jan 27, 2009
Tips for a great answer:
Jan 23, 2016 | Heating & Cooling
Dec 23, 2012 | Heating & Cooling
Dec 23, 2012 | Carrier Weathermaker 8000 Gas Furnace 125k...
Mar 09, 2011 | Heating & Cooling
Sep 23, 2009 | 2003 Land Rover Range Rover
Jan 10, 2009 | Goodman GDS81155CNA Open Flame Mid-Size...
Dec 16, 2008 | Goodman Heating & Cooling
Oct 01, 2008 | Goodman GDS80904BNA Open Flame Heater
40 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: