Question about Goodman CKL24AR24 Air Conditioner
My A/C stopped blowing cold air. So I went to my side yard and check the air conditioner compressor fan was not working. I've check the wires and seem to be fine, I can hear the compressor working but fan not spinning. Any suggestions? Thanks in advance
Do you have a meter? Either the fan is bad or the capacitor is bad. Ohm out the fan and then the capacitor. Be sure you take the disconnect out of the electrical box on the side of the house and or trip the breaker off. The capacitor is a dual run one side operates the compressor and one side operates the fan. I would really bet on the capacitor being bad. Have seen that a lot in my experience. Be sure to make note of the wiring of the capacitor before you take it out to check and if you are not sure how to check it take it to the parts house and they can check it.
Posted on May 17, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 21, 2014 | Mitsubishi Heating & Cooling
Sep 25, 2013 | Dometic Rooftop RV Air Conditioner
Aug 26, 2013 | Heating & Cooling
Aug 03, 2011 | Frigidaire Compact Air Conditioner
May 22, 2010 | LG Heat cool Window Air Conditioner
Sep 16, 2009 | Dometic Rooftop RV Air Conditioner
Sep 04, 2009 | LG Electronic Window Air Conditioner
Jul 29, 2009 | GE Profile ASM10AA Air Conditioner
Jun 30, 2009 | Heating & Cooling
822 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: