Question about Ruud UBHC Air Conditioner
You need to make sure you have 24 volts out of the secondary of the transformer. if you do, make sure that your thermostat is calling for cooling. you'll have 24 volts between the y and c terminals on your board at the furnace.
Posted on May 17, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 10, 2015 | Intermatic Timer T40004RT3 300 Watt Pool...
Mar 15, 2015 | Refrigerators
Feb 25, 2015 | Emerson Heating & Cooling
Aug 18, 2014 | Heating & Cooling
Aug 04, 2013 | Electronics - Others
Sep 07, 2011 | Whirlpool Dryers
Mar 10, 2011 | Heating & Cooling
Feb 17, 2011 | Amana Heating & Cooling
Sep 04, 2006 | GE JVM1490 Convection/Microwave Oven
105 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: