Question about Carrier 38CKC036 Air Conditioner
If you are talking about the indoor blower motor, check the fan switch on your thermostat to make sure that it is in the auto position. If it is, you could possibly have a stuck contact in the thermostat or the relay in the board has stuck open, you can try turning off the power to the unit and resetting it, but I would check the thermostat first. if you have an ohm meter handy, with the power to the furnace off, pull the face off the thermostat and ohm out between r and g terminals on the thermostat, if you have continuity, you know that the thermostat has failed.
Posted on May 18, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 07, 2012 | Desa International Blower Glow Warm Wall...
Sep 14, 2012 | 1999 Buick LeSabre
May 09, 2011 | 1999 Plymouth Breeze
Apr 16, 2010 | 1998 Ford Windstar
Jan 09, 2009 | Kenmore 63942 Dryer
Jan 09, 2009 | 1996 Nissan Pickup
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
263 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: