Question about Honeywell Focus 6300B 5-2 Days Programmable Thermostat Heater
If you have a meter on the indoor unit locate the transformer and check to see if getting 24v ac on the secondary side the primary side should be 220 most of the time their is only one of the wires that would of causes a short red to common the rest just transfer voltage to make the circuit some boards have a 5 amp fuse that will blow and some transformers have a reset button on the 5000 stat make sure that you are putting the wires in correct slots due to having two configurations conventional and heat pump
Posted on May 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 11, 2017 | Honeywell Heating & Cooling
Jan 03, 2015 | Honeywell TH8320R1003 VisionPRO 8000 w/...
Jul 17, 2010 | Honeywell Programmable Thermostat Heater
Nov 26, 2008 | Honeywell Programmable Thermostat Heater
Nov 17, 2008 | Honeywell Programmable Thermostat Heater
Dec 03, 2007 | Honeywell CT3200 5-2 Day Electronic...
Dec 27, 2013 | Honeywell Focus 6300B 5-2 Days...
104 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: