Question about Heating & Cooling
I have an easy fit indoor unit and a pro fit outdoor unit.
the indoor unit has a connector block to connect to the outdoor unit, but the outdoor unit does not have the connector block so which wires go where?
i have 3 wires for power - live, neutral & earth easy enough to figure out but also 2 wires for the 'signal'
the 2 wires for the signal from the indoor unit on the connector block are different colour from the 2 loose wires on the outdoor unit.
Does anybody know which wire goes to which wire for the SIGNAL WIRING only please?
The outdoor unit should have 2 small wires connected to the contactor coil. This delivers the 24v "Signal" to energize the coil. The wire from the t'stat for cooling are usually yellow, in almost every case. When you put the t'stat in the cooling mode and set the temp lower than the room temp, the indoor and outdoor unit should come on. Check for voltage on the terminal block for 24 volts accross the yellow and common wire. Common could be ground on some handlers. If you have the 24 volts, then check for 24v on the 2 small wires (usually 18 to 22 gage wire) on the contactor coil. If no voltage, trace the 2 wires back to the indoor unit and see where they go. If they are the ones that are not attached, put one on the yellow wire terminal and the other on the common terminal. This will send power to the indoor unit and then piggyback to the outdoor unit. Do not remove the yellow and common from the terminal block. Don't be too concerned about the colors from the outdoor coil wires. Just make sure they are hooked up right. Good Luck and hope this gets it going.
Posted on Jun 07, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 05, 2016 | Fujitsu Heating & Cooling
May 29, 2016 | Mitsubishi Heating & Cooling
Dec 05, 2015 | Heating & Cooling
Feb 10, 2014 | LG Heating & Cooling
Jun 15, 2011 | Heating & Cooling
Jan 30, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
May 28, 2010 | Cfm Daikin R410a Split System Air...
Sep 30, 2009 | GE Quiet-Aire Ductless Split System Air...
• Wrong or missing wiring between indoor and outdoor unit cable
• Defect of communication components in indoor pcb assembly
• Defect of communication components in outdoor pcb assembly
• Defect of power supply components in outdoor pcb assembly
• No ground connection in air conditioner unit
(affected by noise in power source)
Jun 30, 2009 | LG Heating & Cooling
Sep 20, 2017 | Heating & Cooling
370 people viewed this question
Usually answered in minutes!