Question about LG LS-K2430HL Heat Cool Mini Split Air Conditioner
Is it possible that a 3.4 HP air conditioner needs only 1.170 KW,when the caculation gives : 3.4 x 0.747 = 2.54 KW ?
Is it possible that an air conditioner of 35000 BTU needs only 1.170 KW when others need twice?
It depends on the (EER) Energy Efficiency Ratio,which is capacity divided by watts.
Example 35000 btus / 2500 watts = 14 EER
If you know the capacity,btus and EER you can calculate the watts, capacity / EER
Example 35000 btus / 14 EER = 2500 watts.
EER is determine by testing the air conditioner at Department of Energy Guidelines, which are
80° drybulb 67° wetbulb indoor and 95° and 82° drybulb outdoor.
Posted on May 15, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 03, 2016 | Sharp Office Equipment & Supplies
Nov 26, 2013 | Frigidaire FRA18EMU2 18,500 BTU Window AC...
Dec 23, 2012 | Casio FX82MS Scientific Calculator
Apr 05, 2012 | Texas Instruments TI-84 Plus Calculator
Aug 04, 2011 | Kenmore Heating & Cooling
Please dont forget to vote if you liked my answer
Feb 12, 2011 | Cobra GPS
Mar 26, 2009 | Casio MS-80TE Calculator
Mar 04, 2009 | Intertherm P3RC-048K Air Conditioner
358 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: