Question about Electrical Supplies
All of the answers you got were all for the same product, it's just being said differently. 2/0 is the correct wire size. I think this question may be old, so you may have already completed your project. By the way, with copper, the voltage drop on an 80 ' run is 0.8 %. On aluminum it is 1.56%.
At any rate, a 150 amp sub-panel with 20 circuits running on a 200 main amp can easily be overloaded. You should probably have a 300 or 400 amp main with a subpanel that large.
Posted on Jun 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 21, 2013 | Bryant /murray Bj2200 Main Circuit Breaker...
Nov 17, 2012 | Electrical Supplies
Oct 06, 2012 | Bryant /murray Bj2200 Main Circuit Breaker...
Sep 26, 2012 | Square D Qo 200 Amp 40 Circuit Indoor...
Nov 13, 2011 | Square Electrical Supplies
Sep 07, 2011 | Cutler Hammer 100 Amp Main Breaker...
Jun 04, 2011 | Heating & Cooling
Aug 19, 2010 | General Electric GE ELECTRICAL TQD22200X2...
Apr 29, 2010 | Bryant /murray Bj2200 Main Circuit Breaker...
Jun 29, 2009 | Electrical Supplies
984 people viewed this question
Usually answered in minutes!