Question about Heating & Cooling
I had the same problem with this unit and had the heater serviced which fixed the problem. The problem is caused by the pilot flame not being big enough to keep the thermocouple hot, so the heater thinks the flame is out and it turns the gas off! The thermocouple is effectively a switch that is on when hot and off when cold. The pilot flame is supposed to keep it hot, so its on and the main burner will get gas. When its off (ie cold) gas is blocked from the main burner for safety reasons! This manual is for a very similar heater: http://www.rinnaisales.co.nz/tradesmart/rinnai2/pdfs/service_info/171.pdf
You need to get at the pilot and clean it out!
Posted on Jul 14, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 19, 2015 | Unitrol Propane Heater Valve - Little...
Jul 15, 2014 | Rinnai Heating & Cooling
Aug 16, 2011 | Heating & Cooling
Jul 18, 2011 | Rinnai Vent Free Gas Heater/
Apr 03, 2011 | Rinnai Heating & Cooling
Aug 23, 2010 | Heating & Cooling
Jul 21, 2010 | Rinnai Heating & Cooling
Oct 17, 2009 | Rinnai Toyostove Direct Vent Heater:...
Mar 13, 2009 | Rinnai Toyostove Direct Vent Heater:...
Jun 19, 2018 | Heating & Cooling
941 people viewed this question
Usually answered in minutes!