Question about Heating & Cooling
What is the Problem?,
Can you discribe, or give more details about the Problem ?
Posted on Jul 03, 2010
Need to know the room temp and out side temp but the expansion valve could be sticking open or the compressor could have bad valves hook up hi side hose to true high side port and shut the liquid valve off in the line set in cooling mode make call for unit to come on and as it pumps down the hi side should go up if not the comp is week but if room temp is 85 or higher and out side about same still low on charge the suction will fall when room cools and the expansion valve quits flooding the coil
Posted on May 10, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 05, 2015 | Heating & Cooling
Aug 05, 2015 | AMVENT 18000 Btu 1.5 Ton Ductless Mini...
Jul 19, 2015 | Cars & Trucks
Apr 20, 2014 | Goodman CLQ36AR49 Air Conditioner
Jun 05, 2010 | LG LSC121PMA Split System Air Conditioner
Jul 07, 2009 | Coleman Heating & Cooling
1.Pump not primed
2.Leakage of air into suction system
4.Valve in suction or discharge line partly closed or suction or discharge line partly plugged or too small. 5.Plugged basket in skimmer or hair in lint strainer.
Jun 06, 2009 | Jacuzzi MAGNUM POOL PUMP 1-1/2 HP MAGNUM...
Apr 19, 2009 | Ruud UBHC Air Conditioner
Nov 01, 2007 | Freezers
1,332 people viewed this question
Usually answered in minutes!