Question about Heating & Cooling
You need to get a qualified 'Gas Safe' engineer to check the Venturi in the flue, and clean it out. The other thing to look at is the igniters, clean them wirth emery paper as this boier relies on flame rectification (ignite and sense flame)
The other important aspect which also hasn't been mentioned is to check the inlet and working pressure (as i have had a faulty gas meter governor before)
Quite often the simple faults are overlooked and everyone goes for the PCB, It is doubtful it's a loose wire on the gas valve, The best advice is to get a gas engineer in and for him to call Halstead while on site.
Be very careful when working on your own gas boiler, as any mishaps, and your house insurance is void.
Posted on Jul 10, 2009
What is the model number? Do you know the fault number?
Posted on May 10, 2009
Posted on Jan 31, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 31, 2015 | Heating & Cooling
Jul 04, 2014 | Water Heaters
Aug 04, 2017 | Heating & Cooling
Dec 28, 2009 | Water Heaters
Nov 30, 2009 | Water Heaters
Nov 14, 2009 | Water Heaters
Oct 05, 2009 | Water Heaters
Jul 04, 2009 | Water Heaters
Apr 03, 2009 | Water Heaters
Mar 31, 2009 | Water Heaters
1,176 people viewed this question
Usually answered in minutes!