Question about Heating & Cooling
Package unit is not marked with manufacturer. I believe it is a coleman, however not sure. I need the wiring diagram for model DAYA-F042N090C. Is anyone fimiliar with this model number and know where I can get the diagram. Compressor is not starting and the diagram is faded. This is a gas package unit. Thanks for any help!
Check the capicitor if it is domed up on top bad check the wires at the compressor to see if burnt take a insulated object and bump the contactor in to see if comp starts if so then out on low voltage circ check for call from stat on common to yellow then follow the connections may be out on low psi switch located in the suction line
Posted on May 10, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 22, 2015 | Coleman Heating & Cooling
Aug 20, 2015 | Coleman Heating & Cooling
May 02, 2011 | Coleman Heating & Cooling
Aug 29, 2010 | Coleman Powermate Premium Plus 6250W...
Nov 21, 2009 | Heating & Cooling
Jun 05, 2009 | Heating & Cooling
May 19, 2009 | Carrier Heating & Cooling
Mar 29, 2008 | Dometic Rooftop RV Air Conditioner
346 people viewed this question
Usually answered in minutes!