Question about Weather King 10AJA6001AH Air Conditioner
The unit is from 2006...
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: outside makes loud noise
I would take a very close look at every solder joint there is between the inside unit and the outside. If you observe oil at any point it indicates a leak at that point. That is an expensive price for what you say was done. Check your invoice for the amount of refrigerant they or he added to the system. Compare it with the amount stated on the outside unit nameplate. Check for frost on the suction (big line) by the outside unit. If there is frost your coil is frozen up. If this is the case turn the fan on and the cooling off. Allow it to run in this manor for about an hour to defrost the A coil. Then return to the cooling mode.
Posted on Jun 16, 2008
check to see if there is a 20 degree split between supply and return air. If its less than 20 than it might be low on charge.
Posted on Jun 24, 2009
When I am called to replace a outdoor fan motor I charge $330.I am in las vegas and the charge varies form company to company.The fan motor itself is approx $80 my cost(230v 1 phase condenser fan motor).
Posted on Jul 21, 2009
what is your suction pressure? 23 degrees is to high on your superheat should be around 10-15 degrees. subcooling a little high. do you have any airflow problems like a dirty condenser or dirty squirrel cage or dirty evapartor? subcooling should be between 10-20 degrees. what is the freon you are using in the unit? what is your delta T? That is the temperature coming out of the supply and return. subtract both of them and you will arrive at your delta t and it should be around 18 to 20 degree difference.
Posted on Jul 02, 2010
Tips for a great answer:
Feb 23, 2014 | ComfortStar CHH012CD-13B Wall Mounted Mini...
on Dec 25, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Aug 30, 2011 | Haier Heating & Cooling
Jul 03, 2011 | Carrier Heating & Cooling
Jun 29, 2010 | Goldstar Heating & Cooling
Mar 05, 2010 | Heating & Cooling
Jan 10, 2010 | Ruud Handle Air Conditioner
Aug 16, 2009 | Sunbeam SCA052MWB1 Thru-Wall/Window Air...
May 09, 2008 | Heating & Cooling
21 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: