Question about Heating & Cooling
My furnace shuts down after one to two minutes prematurely and shows a code of 31 which is pressure switch did not close or reopened the furnace will keep coming on to keep the house warm but will not stay on long enough to reach the demand temp set at the thermo
Try to jump pressure switch as soon as the inducer come on and see if it stay longer. if it does you might have problem with draft or pressure switch itself defected.
Posted on Nov 29, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
check to see if your intake pipe or vent is clear this could cause a flame jump and make it look like a bad flame sensor let me know if this helps
Posted on Jan 08, 2009
The limit switch on the inducer has tripped. There are two wires that go to a small disk about the size of dime that has a small button in the center. Push this little button and you will feel a littl snap and the unit should fire up. Check all the manual reset limits as well. If the unit still won't start, jump the two wires by bypassing the limit switch. If it starts, then replace the switch. Bypassing the switch is only temporary and could lead to death if it is used as a permenant fix.
Posted on Apr 03, 2009
Make sure filters are clean . if they are stopped up the unit will over heat. Lets start there. Russ
Posted on Mar 23, 2010
Testimonial: "James, YOU DA MAN!! I would have never guessed the filters could cause these symptoms. Recent carpet cleaning may have added to filter clogs."
Tips for a great answer:
Dec 16, 2013 | Goodman Heating & Cooling
Dec 17, 2012 | Honeywell Furnace Air Pressure Switch...
Sep 25, 2012 | Bryant Heating & Cooling
Feb 19, 2011 | Heating & Cooling
Jan 23, 2011 | Bryant Heating & Cooling
Jan 04, 2011 | Bryant Heating & Cooling
Jul 27, 2009 | Dryers
Jan 11, 2009 | Honeywell Power Humidifier: Furnace...
139 people viewed this question
Usually answered in minutes!