Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Is it a split system? I had the same problem with my split system and and it was because the condenser line was mounted wrong. The line was mounted so the water had to go uphill and it was causing the condensation to leak through the front of the unit.
Posted on Aug 14, 2007
16. SYSTEM RESET
a. Turn the ON/OFF switch to OFF position.
b. Simultaneously depress and hold the MODE and ZONE
push-buttons while turning the ON/OFF switch to ON.
FF should appear in the LCD display until the MODE
and ZONE push-buttons are released.
c. When a dip switch is turned on or off after initial configu
ration, a system reset will need to be done before the
Comfort Control CenterTM will recognize the updated selection. Try this. This is for the five button thermostat. Did you check the dip switches to be sure the proper ones are turned on? I need to know which stat you have 4 or 5 button. I have trouble shooting for both.
If you notice reset needs to take place after a dip switch is turned on or off. The dip switches are on the circuit board. You need to drop the lower cover. the dip switches will read in this order #1 heat strip/ #2 zone2/#3zone3/ #4 zone4/#5 furnace/#6 differential/#7stag/#8 gen start. Check this out and be careful. Turn off the stat to change dip switches. On will be toward the description. If you don't have remote start gen set the dip should not be on. If you dont have a Zone 3 the dip should not be on, etc.
Any questions feel free to post back
Thank you for using fixya
Posted on Mar 26, 2009
if no cold blowing,evaporator is not working,have you ever heard compressor is running,check this out,no compression of course you dont have cool on evaporator.if the compressor is running check the oprating current,if still have enough freon charge,if not running check thermostat reset setting on the coldest,ifn still not run check overload relay on panel control reset lever to put back compressor to run,check condensing fan if working,if not check also over load protection,this should be done by ac tech nician.have a nice day,dont gorget to rate me, thank's
Posted on Apr 18, 2009
There is a water holding tank on the right lower side (when u are looking at the front), empty it and the unit comes back on.
Posted on Jul 27, 2010
Tips for a great answer:
Jan 25, 2015 | Fujitsu Heating & Cooling
Dec 13, 2014 | Fujitsu Heating & Cooling
May 10, 2014 | Fujitsu Heating & Cooling
Feb 15, 2013 | Fujitsu ASU18RLQ Single Zone Wall Ductless...
Feb 04, 2011 | Heating & Cooling
Dec 27, 2010 | Heating & Cooling
Dec 25, 2010 | Fujitsu 36CS Air Conditioner
Dec 13, 2008 | Fujitsu 18C1 Air Conditioner
Jul 22, 2018 | Thermostats Heating & Cooling
Jul 21, 2018 | Heating & Cooling
20 people viewed this question
Usually answered in minutes!