Question about Heating & Cooling
It could be a thermostat problem. Also it will seem to run constantly as it tries to heat and one of the elements are working which could be a sequencer problem.
Posted on Dec 01, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You should be seeing 120 volts to the igniter. Anything less requires either a replacement of the transformer, start relay or control module.
Posted on May 30, 2008
make sure the thermostat is in the auto mode if so it is more than likely the fan relay control some are built on the board some can be replaced separately
Posted on Dec 17, 2008
first off buy yourself a honeywell stat, in my personal opinion lux stats are garbage, I have run into so many that are bad stats !!! but as far as your fan not shuting down, sounds to me like your fan center on your circuit board is bad and will not shut down the fan when needed, you will have to replace the circuit board, as the fan center is a part of the whole of the circuit board, hope that helps
Posted on Jan 20, 2009
SOURCE: i have a coleman/evcon electric
Have you tried to replace pressure switch for the combustion air. If your not sure where to find it if you pull the front panels off follow the flue pipe down to combustion chamber the combustion fan motor is either inside the flue pipe or out side of it not sure on the one you have but you should see two plastic tubes that connect to a barb onto the topside of the fan and one on the bottom they both should go back to the pressure switch. i hope this helps you if you have any more question or if this doesnt fix the problem just reply back to this message . Make sure fan is working when furnace starts up. It should be the first thing that comes on when there is a call for heat
Posted on Jan 21, 2009
sounds like it is the pressure switch try jumping it out on some models you fool the heater in too working or see if the tubes are blocked , there should be some codes on the front panel or the fan panel
Posted on Apr 27, 2010
Tips for a great answer:
Mar 21, 2017 | Coleman Heating & Cooling
Feb 29, 2016 | Heating & Cooling
Jul 12, 2015 | Coleman Heating & Cooling
Nov 28, 2013 | Heating & Cooling
Dec 28, 2010 | Coleman Heating & Cooling
Jan 18, 2010 | Coleman Heating & Cooling
Nov 28, 2009 | Tools & Hardware - Others
Nov 02, 2008 | Coleman Heating & Cooling
May 30, 2008 | Heating & Cooling
159 people viewed this question
Usually answered in minutes!