Question about Hardware & Accessories
Don't know where the wires go on the relay from the timer
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: gas furnace wont stay lite
I'm a little confused by your terminology. You are saying you have a pilot lite and electric heat strips? Are you possibly meaning burners? Is the heater running for 2 hours straight without shutting off? how cold is it there? Lastly what temperature do you have the thermostat set at and how close does it get to the temp. before it shuts off?
Posted on Dec 20, 2007
I can appreciate in the fact that you do not want to offer a solution to my problem without paying money however you would like me to tell you how I fixed my problem for free, if you would like to know how I fixed it, how about you subscribe to my premium plan and I will tell you.
Posted on Nov 24, 2008
When you call for fan in auto ensure your getting 24 volts at pin on control board, if it is not energizing then there is a problem with the relay.. Before you change out the expensive control board, try the therm..
Posted on Dec 09, 2008
Expensive is relative, service calls are never free. But if you have an idea what the problem is, you are armed against an unethical service company. Now to what you describe, could be a couple things, first let me explain the difference in fan speeds. Furnaces that both heat and cool have multi-speed blower motors. High speed is for cooling and lower speeds are for heating. The fan switch at the T-Stat turns on the high speed fan relay. The lower speed fan is turned on by either a temperature activated switch (silver box mounted on front on furnace above burners) or a time delay relay which is solid state. That being said, your problem could be a defective fan switch or one of your blower motor windings has gone bad. Most motors have 3 or 4 speeds and a technician could just change speeds and all would be good. A fan/limit switch is not so expensive that you would replace the unit. Bottom line, unless your really handy, a heating company is in your future. Good luck and please rate my answer if it was helpful to you.
Posted on Jan 02, 2010
Testimonial: "Thanks. I am not handy when it comes to furnace repairs, however this info will help me when I speak to the tech 1/4. I'll let you know the outcome."
Tips for a great answer:
Nov 24, 2016 | Heating & Cooling
Nov 03, 2013 | Car Audio & Video
Mar 01, 2013 | Lennox Heating & Cooling
Nov 19, 2012 | Heating & Cooling
Apr 14, 2010 | Heating & Cooling
Dec 31, 2009 | Superior Lennox Blower Thermal Sensor -...
Nov 01, 2009 | Heating & Cooling
Dec 12, 2008 | Honeywell Electronic Programmable...
Dec 09, 2008 | Heating & Cooling
Aug 18, 2017 | Hardware & Accessories
25 people viewed this question
Usually answered in minutes!