Question about Fujitsu Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: LG split (3 indoor) LMU360CE
The LED #2 is only flashing while in disconnection or short in Thermistor (3 sec off / 0.5 sec on). If you want to change it, note: this is not an easy job to do! You will need to remove the top panel, then remove the control paneland then the front panel to gain access to the thermistor. The part isnot available to the public and requires an authorized service techfrom LG to take care of this problem. You will need a special tool toremove the front door seal spring clamp.
But you can call customer service @ 800 243 000 and see if theycan transfer you over to parts. Just give them the model and serial #and see if they would be willing to sell you the thermistor part. Youwill also need the door seal spring clamp removal tool to make the jobeasier.
Posted on Aug 02, 2009
This could be caused by a blown circuit breaker or fuse inside the unit, a damaged compressor or fan motor, faulty wires connecting the compressor or fans to the control board unit, a faulty or hung relay on the control board (this can sometimes be solved by tapping the relay with a screwdriver), or the starter capacitor for the compressor or fan motor.
Posted on Sep 20, 2009
Your compressor is seized up. shut down unit and let compressor cool down, it may start again but probably needs to be replaced.... sorry for the bad news,
Posted on Nov 12, 2009
It sounds like your inverter is at fault. You will need an inverter tester ( most good service techs will have one ) to prove that the output to the compressor is correct. If the inverter is okay then it will be the compressor at fault with a location error or it is simply seized. A common fault that caused this was the eev remained closed (coil failure ) and caused the compressor to over heat.
Posted on Jul 15, 2010
SOURCE: fujitsu outdoor unit not working
Its possible there has been a power spike and it has dammaged the power pcb. Remove the cover and inpect the PCB's for blackening. If any blakening replace the damaged PCB.
Posted on Jul 15, 2010
Tips for a great answer:
Nov 17, 2016 | Fujitsu Heating & Cooling
May 29, 2016 | Mitsubishi Heating & Cooling
Jul 10, 2015 | Fujitsu ASU9RLS2 Single Zone Wall Ductless...
Jun 18, 2014 | Samsung AQV36JA Classic 36000 BTU Single...
Aug 03, 2011 | Heating & Cooling
Dec 30, 2010 | LG Art Cool LA121CNP wall/window Air...
Dec 16, 2010 | Mitsubishi MSZ-A24NA Split System Air...
May 11, 2010 | Heating & Cooling
Nov 10, 2009 | Fujitsu 24C1 Air Conditioner
54 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: