Question about Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
check that it is set to cooling sounds like it may be set to heat in cooling mode the indoor fan should at least run
Posted on Mar 13, 2010
Communication error between indoor to out door.Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 02, 2011
To cancel the timer, press timer on setting until it comes 00.00. Or remove batteries from remote and re fix after few minutes. If still problem persists, check and rectify error code of e-5 as follows:
Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 09, 2011
Your split system is an inverter model. In it the compressor is powered not simply from the mains thru a relay but from a special and very complex set of converters: a rectifier to convert the incoming AC current to DC and then uses pulse-width modulation of the DC current within an inverter to produce AC current of a desired frequency to power the compressor.
In your case the unit that provided the final AC current to the compressor has failed. The fact this happened a few days after you have started using it is a clear indication of manufacturing defect - some of the electronic components used in that inverter were of a low quality and they haven't been able to cope with the stresses so they failed.
This is something that only the dealer (and its repair crew) can solve and it's covered by the warranty - time to call them. And in the mean time disconnect the unit from the mains.
Posted on Jun 03, 2011
Tips for a great answer:
Jul 03, 2017 | Fujitsu Heating & Cooling
Dec 27, 2012 | Fujitsu 18C1 Air Conditioner
Sep 24, 2017 | Fujitsu 18C1 Air Conditioner
Jul 25, 2011 | Heating & Cooling
Mar 10, 2010 | Heating & Cooling
Sep 07, 2017 | Fujitsu Heating & Cooling
May 24, 2008 | Fujitsu Heating & Cooling
May 14, 2008 | Fujitsu 24C1 Air Conditioner
Feb 25, 2018 | Heating & Cooling
311 people viewed this question
Usually answered in minutes!