Question about Tech Solution Office Equipment & Supplies
Do you have a manual for the Alerton TS-6000?
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
sounds like your blend door actuator has failed, or the lost vacuum to this actuator, or something got into the vents holding the blend door into position. Most common is the acuator failing, good news is its a fairly inexpensive part, but gettin to it is not fun, its it the ductwork in behind the dash, I'm not sure on your specific model but most I have seen the dash has to come completely out. If it gets to that point you may want a repair shop to do that.But hopefully you get lucky and its easy access.
Posted on Oct 03, 2008
SOURCE: Honeywell Thermostat RTH 7500
Assumed all the wiring are correct,
to change from manual switching from heat to cool, press [system] button ( left ) to go into system setting.
then press and hold the [fan] middle button untill option display 120
use up down button to select option 300 ( Manual/Autochangeover) ,
select 0 for manual, 1 for automatic. ( read caution in page 22 of installation manual )
Posted on Oct 14, 2008
SOURCE: I replaced my Janitrol 7
There should be electric heat strips in the airhandler.
They automatically come on when the unit goes into defrost, the thermostat is turned up more than 7 degrees over the indoor temp or if the outdoor temp is just so cold the HP cannot keep up.
Tat is your auxillary or emergency heat.
What does the new t-stats installers booklet say that the 0170 function and #2 #7 options are for?
If it is for gas vs elec heat then set it on the elec option.
The difference is that in gas heat systems the blower comes on a few min AFTER the furnace fires up to allow the heat exchanger to get hot.
In an electric furnace the blower has to come on emediatly because the heat strips get hot emediatly and if the blower is delayed the system will shut of in high temp overload.
Posted on Dec 18, 2008
your actuatior valva is bad.you can order 1 from auto parts giant online for about 45 bucks the dealer wnats 240.00 that will give the heat and air back
Posted on Mar 08, 2009
when its flashing its in a 5 min delay mode if you wait 5 min and still flashing you may need a new stat. but give it a full 5 min.
Posted on Sep 20, 2009
Tips for a great answer:
Aug 22, 2017 | Goodman Heating & Cooling
Sep 28, 2016 | 2002 Dodge Ram Pickup 1500
Oct 16, 2015 | Heating & Cooling
Jul 25, 2014 | Honeywell Focus Pro 6000 Programmable...
Jul 11, 2014 | Motorcycles
May 13, 2014 | Goodman CLQ36AR49 Air Conditioner
Apr 15, 2017 | Honeywell Heating & Cooling
Jun 14, 2011 | Honeywell CT500 Digital Heat / Cool Manual...
Nov 05, 2010 | Heating & Cooling
Jul 06, 2009 | Dometic Rooftop RV Air Conditioner
Apr 13, 2015 | Tech Solution TS-4500 Shredder
37 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: