Question about Honeywell S8910U Radiator Heater
The furnace does purge, but thats all it does
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Hi, You are right, fan is on a time delay in the heating cycle, and after burners fire that is when this delay comes into play. You have a preset factory temperature that determines the cycle on time for the fan, and the off time after the burners shut down also. This will not be in the thermostat, but in the fan/limit control the is mounted on the face of the furnace, with a probe inserted into the fire box.Depending on how old or new this unit is, will depend on the type control you have.It may be just a high limit switch, or the 1st I mentioned.If so, It rotates in the burner as the temperature rises, to turn the fan on and off.Disconnect power, remove cover, and 2 screws.Slowly remove the control and gently clean the probe. Turn the dial if this one has it and you will be able to hear it click. This click is contacts closing to start fan operation.Reinsert and try again. If problem continues, you will have to replace it.They do tend to stick closed/on, in the heat cycle from time to time and a cleaning sometimes will solve this problem. Not knowing how old this furnace is and type, make it difficult to give you a correct diagnosis, so check this fan control as I have explained, and if your system is of a different type, please let me no so I can correct this problem. Sincerely,
Posted on Dec 11, 2009
you will have to reprogram it according to the operating manual.
The manual is available on www.manualnguide.com
Posted on Feb 02, 2010
Sounds like the switch that controls the blower is faulty. It should heat up then come on at preset temp. As for the stat where is it located. It should be located 60" off the ground not in any direct sunlight and make sure it is insulated behind the stat. You could have more heat loss in those rooms too. IE poorly insulated windows air penetrating through outlets do those walls face the wind? Is the stat located next to a heat supply?
Posted on Dec 16, 2010
Testimonial: "Thank you! I will look into getting the switch checked and verify the stat location. I appreciate your assistance! "
Hello, first turn off power to the Furnace, then remove igniter from bracket and unplug molex connector. Then take the igniter to a Hvac supply store and get new one, reinstall it into bracket plug into molex connector and turn furnace back on.
Posted on Mar 05, 2011
Tips for a great answer:
Aug 04, 2015 | Honeywell Water Heaters
Dec 28, 2014 | Heating & Cooling
Nov 06, 2013 | ICM286 Furnace Control Board
Feb 27, 2013 | Honeywell Furnace Gas Valve Sv9501h2409
Nov 29, 2011 | Goodman Heating & Cooling
Dec 12, 2009 | Goodman GMS90703BXA Heater
Jan 30, 2009 | Goodman GMS90703BXA Heater
Jun 12, 2008 | Heating & Cooling
50 people viewed this question
Usually answered in minutes!