Question about Water Heaters
It is possible that it is airlocked. This sometimes happens on a single pipe system if you run completely out of oil. To remedy the problem you have to loosen the bleeder valve. It is usually locate by the oil line connection to the burner.most of them are shaped to allow connection of a small piece of tubing to direct the oil that will eventualy come out of it to a container . With the unit off, loosen the bleeder valve , then attach one end of the tubing to the valve and put the other end in a small container, turn the unit on .air,foam and bubbles should start to come out of the tubing. Run till a steady stream of oil is present. Shut unit back off, remove tubing and tighten valve, turn unit back on and unit should operate.
hope this helps
Posted on Dec 03, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 01, 2016 | Water Water Heaters
May 03, 2015 | Bosch Water Heaters
Sep 23, 2013 | Honeywell Biasi B10-3 Boiler ,riello...
Feb 02, 2013 | Honeywell Protectorelay Oil Burner Control...
May 21, 2009 | Water Heaters
Feb 01, 2009 | Water Heaters
Nov 12, 2008 | Water RHEEM 40 Gallon FVR PROP PWR Heater...
Oct 13, 2008 | Water Heaters
Aug 14, 2017 | Water Water Heaters
35 people viewed this question
Usually answered in minutes!