Question about Cooper Industries Cooper Wiring 2158V 3 Gang 2 Toggle Switch- Duplex Wallplate, Ivory
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
WARNING: Do not attempt to do this work unless you completely understand the information provided below. If in doubt call an electrician.
Always make sure the power is disconnected from all possible sources before making any connections. Your description of the problem indicates that there may be multiple power wires coming into the same box. In that case local codes may require that the box be partitioned to prevent exposure to voltages up to 220 volts.
You need to determine where each wire goes to know how to connect them together. You cannot rely on color alone. If the power supply runs through the box to the loads then most (but probably not all) of the white wires will be connected together. If the power runs to the load boxes first then none of the white wires in the switch box should be connected together. They are used to run the switched/dimmed power back to the loads (and should be taped to cover the white in the box). In that case each switch has its own power input and they should not be tied together. A wire (could be black or white with black tape) brings power from the load box, gets connected to the input terminal of the switch and the corresponding black wire carries the switched power back to the load. The fan/light switch will have one power in and a switched power out for the fan and another for the light. The 3-way will have one "power" in (or it could be the final power out to the light) and two "carrier wires that connect to the other 3-way switch. If the power supply goes through the switch box then there will be at least 10 wires in that box. In that case see the attached diagram:
Posted on Sep 23, 2009
before u start make sure power is off before working with electrical lines ---start with the 12/2 coming into box black [power] white [ground-neutral] and u will have 3 separate lines for the lights so u will have 4 lines total coming in the box== with the 3 light lines take the white and strip back the plastic and connect [wire nut] all 3 to the 12/2 white line --now take the 12/2 black line and connect it to the first switch gold color screw- bottom screw -now take some wire about 2-3 inch strip both ends and connect from the 12/2 black wire connection on the switch and connect to the gold /bottom of switch 2 than do the same for switch 3 connecting the wire from switch 2 so u will have power feeding all 3 switches-- now connect the black lines for the lights to the other side of each switch and ur done
Posted on Feb 14, 2010
Tips for a great answer:
Sep 16, 2014 | Electrical Supplies
Feb 26, 2013 | Electrical Supplies
Nov 19, 2011 | Home
Jul 04, 2011 | Casablanca Fan (88U33M) Ceiling
May 28, 2011 | Cooper Industries Cooper Wiring 2158V 3...
Feb 14, 2010 | Cooper Industries Cooper Wiring 2158V 3...
Feb 08, 2010 | Dryers
Jun 17, 2008 | Hampton Bay 24002 Ceiling Fan
57 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: