Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I have a goodman GMP075-3 that won't turn on. I think it is the pressure switch since I do not have a vent blockage. What is a venter and where can I find it??
Posted on Dec 30, 2008
i think the ca # is for the cooling coil unit - the heater should start with gmXXXXX - if your unit is fairly new - the pilot light electronically when thermostat calls for heat the unit will not light if the burner door is open
Posted on Oct 24, 2009
Heat pumps provide good heat until the tempurature drops below 35-40 degrees. After that there isn't much heat to extract from the outside air and then either the gas furnace kicks in or the electric heat strip does the job of heating the air. if you have heat strips, I would check your breakers in your panel and sometimes there are a couple of breakers right on the air handler or furnace. The ones that will be for your heat strip are 220v and will be twice as wide as your normal 110v breakers . Please don't trust a visual inspection as they can look like they are in the "on" position but are indeed tripped. Turn them all they way off and then back on. If the beakers check out you may have an open cicuit in the heat strips themselves and you will need to have a qualified HVAC tech look at your furnace to repair it.
If your furnace is a "duel fuel" and uses natural or LP gas for back up heat then your ten year old rheem probably needs a good maintenance by a qualified service tech. There is a flame sensor to clean, ignitor to check (replaces the old school pilots), burners to clean flue connections to check and much more. ALL manufacturers of any heating apliance recommend yearly maintenance. Most companies offer something for around 100 bucks. I hope this helps.
Posted on Dec 13, 2009
Testimonial: "Rocco, this was the most thorough and helpful response I've seen from anyone so far... I tried justanswer.com and they really didn't help like this.TX"
It sounds like the problem is a tripped limit switch. Look in the burner compartment and on the blower assembly for a switch that looks like the one below. It will be about the same size round as a quarter. Press the red button on any of the switches you find, then re-try furnace.
Posted on Mar 23, 2010
Possibly overheating or previously overheated, these units are also prone to control box issues usually a buzzing noise at the unit it present if this is the case.
Posted on Apr 28, 2010
Tips for a great answer:
Oct 24, 2015 | Goodman Heating & Cooling
Jul 23, 2014 | Goodman Heating & Cooling
Jul 25, 2017 | Goodman GDS81155CNA Open Flame Mid-Size...
Apr 23, 2011 | Goodman GDS81155CNA Open Flame Mid-Size...
Feb 21, 2011 | Goodman Heating & Cooling
Jan 04, 2010 | Goodman Heating & Cooling
Jul 29, 2009 | Goodman CKL24AR24 Air Conditioner
Nov 08, 2007 | Goodman GMS90703BXA Heater
Sep 26, 2017 | Honeywell Heating & Cooling
Sep 25, 2017 | Heating & Cooling
25 people viewed this question
Usually answered in minutes!